No power on output
can someone help me with this?
There si 0V on AC and i dont know why.. invertors are conected to 230V 50Hz.
Panels are not original from UBNT.
FW on gateway is 1.0.2
Do you have the EU End Run Model number SM-EC-EU installed and configured as well with the correct country code selected?
The panel specs look fine, as Aaron said if you have an EU end run, it needs to be adopted so that the correct parameters can be sent to it from the gateway.
Did you set the country and region for gateway and MI? You should be able to set it as below picture, if you are not sure what region to set, then try Australia for 50Hz first.
I think i have everything correctly.
I have try to all regulations from EU and nothink changes.
I need END RUN too ? I have now only picoGW and 2 Invertors.
Can you picture the wires how you connect MI to grid to us? Better with detail to the color of wires.
My colleague forgot sent me QR Code of ENDRUN device.
But now it is another problem. Today is little cloudy day and inverters sometimes stops producing electricity.
We dont need peak prodictivity but as long as possible current.
some photos from tele. mast
Please try to set your system as Australua region, it's a wider range setting for grid, then you should be able to see better current. That's also means the power quality is not so well at where you are.
If it's possible, please also connect gateway to internet, and set the gateway as port 22 forward to internet, by that I could access into the gateway to check the problem.
Dude all works fine with Australina regulacy RegionAS-4777 (230V/50Hz):)))
Ty for respone and support from everyone!
Best regards !